One of the Codeflex servers is currently having connectivity issues which is causing some websites to be unreachable. We have contacted the data centre in regards to this, and hope to have an update soon.
UPDATE 8.30PM: The data centre have responded that they are having issues with a rack full of servers - they are currently working on this issue and hope to have it sorted soon.
UPDATE 9.00PM: Service is now restored. Something in the rack caused both breakers to trip killing power to the rack. Once power was restored, the network switch had issues which had to be rectified.
Tuesday, July 16, 2019